Smoke alarms Brisbane
Smoke alarms can save your life. However, you must make sure they are working perfectly and installed properly. Our team of Fully Qualified Master Electricians can ensure proper smoke alarm installation according to Australian Standards. We make sure that the alarms will give you the warning during emergencies. It is your safety which is why there is no reason to delay this.
The team at Eco Electrical Services Brisbane will do the installations and make sure the visual and audio indicators are working as they should be. It is difficult to know if the smoke alarms are indeed working by just looking at them.
What should be done is to allow our professional electricians inspect the smoke alarms. Regular smoke and heat alarms are not suitable for everyone, and not everyone can respond or escape quickly if there is a fire. However, there are different kinds of fire detection and prevention systems available to help keep everyone safe.
Call Eco Electrical Services Brisbane today to find your best suited option for Smoke Alarms in your Business.
Your Complete Electrical Service Technicians!
We stand by our workmanship and take pride in all of our jobs. With our expertise and experience we can give you professional cost saving advice, affordable solutions and 5 star service. All of our technicians are Licensed and trained in the latest technology.
Free Quotations and Upfront Pricing
Need a price? We like to be upfront too.
For your peace of mind we have upfront pricing and offer Free Quotes for those tricky jobs.
Estimates Over the phone where we can.
Please call us to discuss your job and we can give you an idea on price over the phone.
Communication is key
Jobs go smoothly when there’s great communication. We explain every step and ensure you understand the process before we start. If something arises during the job, we’ll run through the options before we start.
We work to all Budgets
Small & Large jobs. Call us today to discuss your project, Sam and his team will look after you…
From 1 January 2017
All new homes or units and substantially renovated homes or units that are subject to a building application submitted from 1 January 2017, will require the installation of hardwired, photoelectric interconnected smoke alarms.
- Smoke alarms in the dwelling must:
- be photoelectric (AS3786-2014); and
- not also contain an ionisation sensor; and
- be hardwired to the mains power supply with a secondary power source (i.e. battery); and
- be interconnected with every other smoke alarm in the dwelling so all activate together. The legislation requires smoke alarms must be installed in the following locations:
- on each storey
- in each bedroom
- in hallways that connect bedrooms and the rest of the dwelling
- if there is no hallway, between the bedroom and other parts of the storey; and
- if there are no bedrooms on a storey, at least one smoke alarm must be installed in the most likely path of travel to exit the dwelling.
Get The Facts – (Download PDF)
We are legendary for our fast response to all emails, however if you need anything urgently please call us on
About photoelectric alarms
Photoelectric smoke alarms, detect visible particles of combustion and respond to a wide range of fires. Any existing smoke alarm being replaced from 1 January 2017 must be a photoelectric-type alarm which complies with Australian Standard 3786-2014. If a smoke alarm which is hardwired to the domestic power supply needs replacement, it must be replaced with a hardwired photoelectric smoke alarm. In existing domestic dwellings, it is possible to have a combination of smoke alarms (240v and battery operated) and interconnectivity can be both wired and wireless.
Smoke alarms must not be placed within:
- 300mm of a corner of a ceiling and a wall
- 300mm of a light fitting
- 400mm of an air-conditioning vent
- 400mm of the blades of a ceiling fan.
There are special requirements for stairways, sloping ceilings, and ceilings with exposed beams. Every dwelling is different so you will need to assess yours. Avoid installation in the following positions:
- in dead air space. This is an area in which trapped hot air will prevent smoke from reaching the alarm. This space generally occurs at the apex of cathedral ceilings, the corner junction of walls and ceilings, and between exposed floor joists.
- near windows, doors, fans or air-conditioners. Excessive air movement may prevent smoke and gases from reaching the smoke alarm or cause nuisance alarms.
Accidental alarms can be a nuisance and become dangerous if home owners remove the alarm batteries or disable an interconnected system to silence the alarm. Nuisance alarms can be avoided by not placing alarms in or near kitchens where cooking smoke can set them off, or in or near bathrooms where steam often causes accidental alarms. Also avoid insect infested areas, as insects flying into the alarm can trigger an alarm.